Zhejiang Jieneng Compression Equipment Co.,Ltd.
Km.ssor Water lubrication oil-free screw compressor maintenance
☆Check and record the water level before starting and during normal operation.
☆Inspection records of the compressor discharge temperature, such as higher than 60 ℃, should contact the manufacturer.
☆Inspection records for leaks, abnormal noise, etc., contact the manufacturer of any abnormality.
☆Record total daily running time and load time. Periodic replacement water filter cartridge. Periodic replacement of the air filter.
Km.ssor Micro-oil screw compressor maintenance
☆Check the oil level before starting and during operation is normal.
☆Check the compressor discharge temperature, such as higher than 93 ℃, to clean the radiator.
☆Check whether the oil spill, abnormal noise and, if abnormal timely response.
☆Clean the machine once a day, to ensure that the machine is free of dust, oil.
The first 500 hours of operation to replace oil, oil filters, air filters, for the first maintenance. After the regular oil change, oil filter, oil separator, air filter.
1.This machine is strictly prohibited reversed, turning the compressor must be checked for compliance before the first boot.
2.Unit must be grounded, or it may have a major accident.
3.Not be changed without the written permission of the manufacturer to set parameters, or it may have a major accident.
4.Km.ssor En must replace original parts and lubricants, or it may have a major accident and loss of free warranty.